Hany SamyI do not find what I can say and I do not know how to thank you. It was a great week with you and it was one of the best times I ever had. your boss is excellent and the factory is very good I'll miss you all I miss you so much Thank you Hany samy
HazelThank you very much for the training and for being generous hosts. We have learned a lot and will be putting our knowledge into good use. Regarding the specs for our sample model, we’ll get back to you once we have gathered more information. Again, thank you for accommodating us in the training J
WenThanks for the hospitality during our visit to your company. We are waiting for your revise offer with inclusive shipping cost. Thanks.
QJ series Deep Well Submersible Pumps Stainlees Steel 304 / 316 / 316L
|Protection Class||IP68||Medium||Fresh Water|
|Driven||Electric Motor||Material||Cast Iron, SS304/316/316L|
|Isulation Class||F||Rated Voltage||220V/380V/440V/460V/660V|
SS316 Deep Well Submersible Pumps,
SS304 Deep Well Submersible Pumps,
Submersible Vertical Turbine Fire Pump
Submersible Pump Deep Well Submersible pumps stainlees pumps
QJ series submersible pumps includng QJ deep well (borehole) submersible pumps, QJH stainless steel
submersible pumps , QJT bottom-suction submersible pumps and QJR hot water submersible pumps .
These series of submersiable pumps are mainly used in drawing water from well , river, sea and lake,
farmland/spray irrigaion, aquaculture, water supply or drainage system for cities, industrial and mine est-
ablishements, drawing water from hot spring, fountain projects and so on.
|Frequency||50hz / 60hz|
Non-conrrosive medium: Castiron HT200
Mildly or moderately corrosive: Stainless steel 304
Strongly corrosive: Stainless steel 316 or Stainless steel 316L
1. The three-phase power supply voltage deviation does not exceed ±5% and the frequency deviation is not
more than ±1%；
2. Motor cavity must be filled fullly with clean water during operation.
3. The first stage impeller of the pump shall be immersed at least 2 meters below the dynamic water level.
The pump unit shall not be more than 70 meters below the static water level. The bottom of the motor
shall not be less than 3 meters from the bottom of the well.
4. Ensure the source of water is enough for pump operating continuously.
5. If it is used in pool, should add guide tube fro pump motor in order to cooling.