Hany SamyI do not find what I can say and I do not know how to thank you. It was a great week with you and it was one of the best times I ever had. your boss is excellent and the factory is very good I'll miss you all I miss you so much Thank you Hany samy
HazelThank you very much for the training and for being generous hosts. We have learned a lot and will be putting our knowledge into good use. Regarding the specs for our sample model, we’ll get back to you once we have gathered more information. Again, thank you for accommodating us in the training J
WenThanks for the hospitality during our visit to your company. We are waiting for your revise offer with inclusive shipping cost. Thanks.
Big Flow 4 Stage Vertical Shaft Turbine Fire Pump , 4500 Usgpm Deep Well Pump
|Use||Deep Well Pump||Casing||Ductile Cast Iron|
|Bearing Housing||Cast Iron||Speed||1760rpm|
vertical fire pump,
vertical turbine centrifugal pump
Big Capacity 4 Stages Vertical Shaft Turbine Fire Pump 4500 Usgpm Deep Well Pump
Vertical shaft turbine (commonly referred to as “vertical turbine”) pumps are unique in that the impellers are intended to be submerged in the water source. They are used for installations where the water source is below the pump impellers.
These pumps have a bowl assembly which contains several impellers on a vertical shaft – where the discharge of one impeller directly feeds the suction of the next impeller, and so on – a column assembly built to a specified length, and a discharge head assembly which holds the motor or right-angle gear drive. In a mechanical room, the discharge head assembly of a typical vertical turbine pump is the only visible part of the pump.
This pump does come with a few disadvantages. Besides the additional initial cost, these pumps can be challenging to service. One must remove the pump or disassemble it, which often requires use of a roof hatch in a room so that a crane can lift it out for examination. Since these pumps are all custom-built, the lead times can also be long – from 8 to 20 weeks depending on the manufacturer and models.
Special care must be made before operating a vertical turbine pump for the first time – the shaft and impellers must be properly adjusted to lift them off of the bowl casings prior to operation.
The VTP pump line is normally designed to operate in wells or sumps. Its bowl assembly consists primarily of a suction case or bell, one or more pump bowls and a discharge case. The pump bowl assembly is positioned in the sump or well at a depth to provide the proper submergence.
- Capacity up to 13,636 m³/h (60,000 U.S. gpm)
- Head up to 762 m (2,500 ft)
- Maximum Pressure 74 bar (1,080 psi)
- Temperature 0 to 121 ºC (32 to 250 ºF)
Deep well, irrigation, sumps, condensate, can pump requirements, fire service, municipal, industrial
NM Fire is the firt member of NFPA from Chinese pump manufacturers. The production of fire pump groups is strictly in accordance with NFPA20, production process and performance testing also meet the requirement of ISO9001, some kinds of products have got APSAD (France), UL,FM and CCCF certificates.
We are the only enterprise in China that obtained not only UL and FM certificates, but CCCF as well, also the firt company in the world who was authorized by UL CCIC as witness testing center for both fire pump and fire fighting engines.
|1. To supply high-quality products with reasonable prices in food additive industry.|
|2. To follow orders and arrange shipping in time, providing complete documents|
|for Customs clearance according to different export policies in different countries.|