Hany SamyI do not find what I can say and I do not know how to thank you. It was a great week with you and it was one of the best times I ever had. your boss is excellent and the factory is very good I'll miss you all I miss you so much Thank you Hany samy
HazelThank you very much for the training and for being generous hosts. We have learned a lot and will be putting our knowledge into good use. Regarding the specs for our sample model, we’ll get back to you once we have gathered more information. Again, thank you for accommodating us in the training J
WenThanks for the hospitality during our visit to your company. We are waiting for your revise offer with inclusive shipping cost. Thanks.
NMFIRE 500 GPM Electric Motor Driven Split Case Fire Pump UL FM
|Application||Fire,water,municipal Water Supply Etc.||Structure||Single-stage Pump,Multistage Pump|
|Pressure||High Pressure,Low Pressure||Power||Electric|
|Theory||Centrifugal Pump,Horizontal Split Case Centrifugal Pump||Warranty||1 Year|
|Rated Flow||500 GPM||114 m³/h|
|Speed||2980 rpm / 3550 rpm||50hz/60hz|
|Head Range||35m ~ 433m|
|Driven||Electric Motor||Techtop UL Listed|
|Pump Type||Horizontal Split Case||NMFIRE UL/FM|
|Control Panel||Electric controller||Tornaech UL/FM|
|Medium||Fresh water / Sea water|
NMFIRE 500 GPM Electric Motor Driven Split Case Fire Pump
Fire pumps are used to supply water for automatic sprinkler systems, standpipes or fire hydrants.
NMFIRE Split case are pumps are rated 300, 450, 500, 750, 1000, 1250, 1500, 2000, 3000,
3500, 4000, 4500, 5000, 5500, 6000, 6500, 7000, 7500 and 8000 GPM. All fire pumps are rated
at 40 pounds per square inch or more of boost.
Fire Pumps of the type described shall meet the following basic requirements:
1. Each pump is to be tested hydrostatically for not less than 5 miniutes. The test pressure is to be
not less than 1.5 times the max. working pressure of the pump, but in no case less than 250 psi
2. A pump shall develop not less than 65 percent of rated total head when discharging at 1.5 times
rated capacity. The maximum net pressure for a fire pump shall not exceed 140 percent of rated
3. The maximum pump brake horsepower shall not exceed the HP rating its driver, including service
NFPA 20 requires all fire pump motor drivers to be rated for continuous duty and sahll not be used at
voltages in excess of 110% of rated voltage. At rated voltage and frequency, the full load ampere rating
shall not be exceed (excepts as allowed by the service factor on motor nameplate) under any pumping
The motor control panel equipment shall be factory assembled, wired, tested, and spcifically approved for
fire pump service. Combined manual and automatic type to incorporate the following:
a. Isolating switch
b. Externally operable, quick breaking disconnect
c. Time delay locked motor over current protection set at 600% of motor full load current for 20 seconds.
d. Pressure switch with high and low pressure setting
e. Motor starter of the magnetic type
f. Pilot lamp to indicate circuit breaker closed and power available
g. Phase revversal visible indicator pilop lamp.
STANDARD EXPORT SEAWORTHY PACKING