Hany SamyI do not find what I can say and I do not know how to thank you. It was a great week with you and it was one of the best times I ever had. your boss is excellent and the factory is very good I'll miss you all I miss you so much Thank you Hany samy
HazelThank you very much for the training and for being generous hosts. We have learned a lot and will be putting our knowledge into good use. Regarding the specs for our sample model, we’ll get back to you once we have gathered more information. Again, thank you for accommodating us in the training J
WenThanks for the hospitality during our visit to your company. We are waiting for your revise offer with inclusive shipping cost. Thanks.
UL/ FM Tornatech Fire Pump Controller for Diesel Engine Fire Fighting Pumps
|Function||Diesel Engine Control||Brand||Tornatech|
|Origin||UAE / CANADA||Application||Fire Fighting|
jockey pump controller,
diesel pump control panel
UL/ FM Tornatech Controller For Fire Fighting Systems
Diesel engine fire pump controllers are designed to automatically start a diesel engine driven fire pump upon
detection of a pressure drop in the fire protection system. A diesel engine fire pump controller provides automatic &
manual starting and stopping. An automatic start is controlled by a pressure transducer or by remote automatic
devices as deluge valve. A manual start is controlled by remote manual button or by controller pushbutton. The
automatic shutdown option provides a 30-minutes automatic stop after automatic start once all starting causes have
returned to normal. The diesel engine fire pump controller includes two battery chargers to maintain the engine
batteries continuously charged.
Types of Diesel Engine Fire Pump Controllers
METHODS OF STARTING
The controller will start automatically on low pressure detection by the pressure sensor when pressure drops below
the cut-in threshold. The controller must be in automatic mode.
The engine can be started by pressing the CRANK 1 or and/or CRANK 2 push button, regardless of the system
pressure, when the Main Selector switch is in the HAND position. The Fuel Solenoid Valve will open as soon as a
CRANK button is pressed and will remain in this state.
REMOTE MANUAL START
The engine can be started from a remote location by momentarily closing a contact of a manual push button.
REMOTE AUTOMATIC START, DELUGE VALVE START
The engine can be started from a remote location by momentarily opening a contact connected to an automatic
device. The controller must be in automatic mode.
In case of multiple pump application, it may be necessary to delay the starting of each motor in case of water
pressure drop to prevent simultaneous starting of all motors.
FLOW START, HIGH ZONE START
The controller can be started by opening/closing a contact on the FLOW/ZONE START/STOP input.
The engine can be started (and stopped) automatically at the preprogrammed time.
The motor can be started automatically for a preprogrammed time by pressing the run test button.
METHODS OF STOPPING
Manual stop is done by pressing the STOP push button. Note that pressing the stop push button will stop the
engine only if all starting causes have disappeared.
The automatic stop is possible only after an automatic start and this function must be activated. When this function
is enabled, the motor is automatically stopped 30 minutes after the restoration of the pressure (above the cut-out
threshold) given that no other run cause is present.
FLOW STOP, HIGH ZONE STOP
If the controller has been started by the FLOW/ZONE START/STOP input and that the signal has returned to
normal, the motor will be stopped given that no other run cause is present.
The emergency stop is always possible in any running condition and is done by positioning the main selector switch
to the OFF position.